Rivated Hollow Steel Raised Foor with Flat Covers-507 is composed of Unipanel, Base Connector, Central Cap, Flank Cap and pedestal. There is an installation area surrounding the panel with the width of 14mm and height of 3.5mm lower than the panel surface. Each of the false floor has four screw bars. Base connetor is used to connect the area between panels laid out by panel, central cap and flank cap. The metal slots can be installed under the cap. Each of the corner is supported independently and slot cover board is paved evenly. Wires can be pulled out or socket can be installed at any point around the panel.
Linkfloor Network Panel System (RP-LF507)
Module Set size: 600mm×600mm=1 UniPanel + 1 Base Connector + 1 Central Cap + 4 Flank Caps
System height: 40mm-150mm
Main Components of data center raised floor
Top and bottom plate of panel:
Steel, corrosion protection with powder coating
Steel, corrosion protection with electro-deposition
Riveted structure that is high strength and light weight
Edges: 3.5mm recession, 14mm width at panel borders
Pedestals: Galvanized steel, fixed at four corners. Assembled to system's required height
Base connector: Galvanized steel. Used to connect UniPanel's pedestal, and automatically form the standard-distance cable trenches
Central cap: Size: 196mm×196mm
2mm thick steel, corrosion protection by powder coating or electro-deposition. Re-enforced ribs Installed at the intersection of the cable trenches.
Flank cap: Size: 200×126mm
2mm thick steel, corrosion protection by powder coating or electro-deposition. Re-enforced ribs to install on the cable trench.